Kitchen Grease Separators - Free Standing Installation
With complete disposal
With partial disposal
- Mobile separator for food stall or marquee
- Basic design for disposal via the cover
- Extension stage 1 for disposal via direct suction
- Extension stage 2 with manual high-pressure interior cleaning and optional disposal pump for disposal without odour build-up
- Extension stage 3 with automatic high-pressure interior cleaning and optional disposal pump and remote control for disposal without odour build-up
- Available in oval curved or split design for optimal installation
- Optionally available in manual or automatic design.
The industrial sources of waste water must ensure through appropriate pretreatment facilities that substances and liquids, which spread noxious fumes and nuisance odours, affect building materials and drainage systems or interfere with the operation, will not enter public pipes. In establishments where grease-containing waste water accumulates, grease traps according to EN 1825/DIN 4040-100 must be installed to guarantee the retention of greases and oils of an organic origin from the waste water. This applies, for example, for kitchen operations and meat processing plants. A double lifting plant or complete pumping station must be provided after each grease separator that is installed below the backflow level (generally the street level).
The individual requirements placed on grease separators, lifting plants and complete pumping stations require adjustable product in various sizes and materials.
ACO Haustechnik had an extensive product range of grease separators, lifting plants and complete pumping stations for the ground installation and free-standing installation for decades.
The standards and tests
All grease separators by ACO Haustechnik are produced according to the applicable standards EN 1825 and DIN 4040-100. The grease separators listed in the product range are hydraulically tested and have a general official approval, i.e. the new application permit from DIBt Berlin. The separator systems furthermore are subject to a routine inspection by the Landesgewerbeanstalt Bayern that checks the separator production for the adherence to the currently applicable test standards.
Kitchen Grease Separators - Underground Installation
Commercial operations generating wastewater must implement appropriate measures, by using suitable pre-treatment installations like separators, to ensure that solids and liquids which can give off toxic and unpleasant vapours and odours are prevented from damaging construction materials and drainage facilities, harming operations, and are held back so that they do not enter sewage pipes.
Quality standards and tests
All ACO Grease separators are manufactured in accordance with EN 1825, all ACO Light liquid separators are manufactured in accordance with EN 858. All the separators in the range are hydraulically tested and have General Building Supervisory Authority Authorisation and/or the new application authorisation from DIBT Berlin.